Prolojik’s PN462BLE is an intelligent routing and power distribution hub for PS462BLE sensors. Proxima sensors are either internetworked using CAT 6 patch leads or 4 core (2 pair) cable. In both cases the cable provides LON connection and 12V DC power to each sensor.
The CAT 6 can be connected between up to 10 BLE sensors then back to the PN462 hub. Multiple branches of 10 sensors up to a maximum of 64 can be networked back to any one hub.
At the electrical riser, The PN462 connects to an area controller panel containing a high efficiency 12V source and an IP router (sold separately).
The panel will have a termination port for each of the 4 Cat 6 home run cables or for the 4 core (2 pair) cable.
Input Voltage: 2VDC.
4 x RJ45 home-run ports.
Output Voltage: 12V DC
16 x RJ45 outbound ports.
Each output is fused at 2A.
When the 4 core (2-pair) cable is used, the installer must ensure that cable terminations are correct and pre -tested before connecting to the 12 V power supply.
Mixed or reverse polarity will not damage the equipment, but will prevent commissioning until the fault is cleared.
We recommend a maximum run length of 60m f rom the PN462 hub to minimise volt drop.
The PN462 hub shall in turn be wired back to the electrical riser using up to 4 uplink ports.
The criteria shall be as follows;
Quantity of Sensors on Hub
Where the home run is implemented on a 4 core (2-pair cable), a 16AWG or 1.5mm cross sectional are cable should be used for the 12V connection.
Termination: 16 x FCC68 8×8 ports for PS462BLE Proxima Sensors.
Operating Temperature; 0 °C to +50 °C.
Operating Humidity: 95% RH, non-condensing.
Storage Temperature: -40 °C to +85 °C.
Operating Altitude: 3000 m
Emissions: EN55022 class A conducted & radiated(1).
Immunity: Compliant with EN61204-3:2000 high severity levels.
Harmonic Currents: EN61000-3-2 class A; EN61000-3-2 class C for loads >20%.
Voltage Flicker: EN61000-3-3.
ESD Immunity: EN61000-4-2, level 3, Perf Criteria A.
Radiated Immunity: EN61000-4-3, level 3 Perf Criteria A.
EFT/Burst: EN61000-4-4, installation class 3, Perf Criteria A.
Surge: EN61000-4-5, level 3 Perf Criteria A.
Conducted Immunity: EN61000-4-6, level 3, Perf Criteria A.
Dips & Interruptions: EN61000-4-11, 30% 10 ms, 60% 100 ms,100% 5000 ms, Perf Criteria A, B, B. Semi F47 Compliant.
Safety Approvals: IEC60950-1: CB Report, CSA-C22.2 No. 60950-1-05, UL60950-1, TUV EN60950-1.